I would like to configure a 0 - 10 V input, but there is no setup option.
The available options for the measurement range depend on the hardware configuration.
This can be changed by altering the positions of two jumpers.
For the ranges -10 / 0 / 2 - 10 V, the jumpers on the CPU board (inputs 1 and 2) or the input board (inputs 3 and 4) must be set as follows:
Making settings through the setup program will only be possible if the jumpers have been set accordingly.